What is the minimum waiting time/ refresh time between the each polling to Tesys U Modbus Communication Module LULC033.
For TeSys U the data update or refresh on PLC will be more related to the networks use. Some networks have faster exchange
data rate than other.There are 2 situations for TeSys U but in both situations the slowest part of communication will be network
in regards of number of data requested and number of slaves.
1) On association LUCB + LULC** the data are directly transmitted to communication module and refresh time is around
30ms on LULC* register.
2) On association LUCM + LULC**the refresh cycle between control unit and communication is around 150ms and after
transmitted to LULC register