Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Schneider Electric India Website×
For M238 controller,
Memory area 1 is dedicated to %IW (Input registers) and its limitation is up to 512 words.
Memory area 2 is dedicated to %QW (Output registers) and its limitation is up to 512 words.
So, maximum 512 words of %IW and maximum 512 words of %QW can be used in M238 Modbus IO scanner.
Attempt to use more than 512 words for %IW or 512 words for %QW will result in Build error while performing "BUILD ALL" .
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!