Schneider Electric India Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
EF2 is the Ground Fault.
if the motor cable is longer than that specified for the drive size, it will increase the magnitude of the earth leakage current, due to stray capacitance and trip the drive.
The possible solutions are:
1. Check the motor and motor cables for ground faults.
2. The use of motor choke to reduce the level of dv/dt.
3. If it's the installation is in industrial and the cable is shielded find out if you can remove the earthing for the cable.
4. Try to reduce the switching frequency and note the difference.
5. Also good choice is to disconnect grounding capacitors by pulling out disconnecting switch. Refer attached document.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!