|FA232863||What is the default IP address to open Com'X 200 configuration pages.|
Com'X 200 address: 10.25.2.1 if you connected through WiFi, or 10.25.1.1 if you are connected through Ethernet Cable.
|FA232862||What are Auxillary Power supply options for Com'X200 Energy Server.|
The Com'X200 comes with 3 ways to get powered:
100 -> 230VAC (+/- 15%)
24VDC (+/- 10%)
|FA232861||How to do factory resetting of Energy Server Com'X 200|
Factory reset procedure;
Power ON Com'X 200
As Com'X 200 is starting (Power LED is still yellow), press simultaneously the two front buttons...
|FA232859||What is the different between running the self test "automatically" and "manually by pushing T button" on IM400 vigilohm device.|
The both test are the same i.e. by running the self "automatically" and " Manually at any time by pressing the T contextual menu button on one of...
|FA232858||What are the internal test carried out by Vigilohm IM400 in Autotest.|
The Autotest carried out by Vigilohm IM400 device detects indicator lights, internal electronics, and alarm relays.
|FA232857||Does PowerLogic PM5000 series meter has Instrument Transformer correction (ITC) feature. If not, which meter model has ITC this feature.|
Instrument Transformer Correction (ITC) allows you to correct for inaccuracies in the current transformers (CTs) and potential transformers (PTs).
|FA232856||What are the types PowerLogic PM800 I/O module available & there characteristics.|
See below PowerLogic PM800 I/O modules available & there characteristics;
|FA232855||How to configure the I/O configuration for PM850 via. front display panel for Analogue output 1 --> Real Power & Analogue Output 2 --> Average current|
Refer below steps to configure the Analogue output channels;
1. Navigate to setup tab of Analogue output configuration (Maint -->Setup --> A/O)
|FA232849||What is the powerlogic PM820 meter life of the internal battery-backed clock.|
The power meter uses its nonvolatile memory to retain all data and metering configuration values. Under the operating temperature range specified...
|FA232129||What is a Process Hazard Analysis (PHA)|
A PHA is an OSHA directive that identifies safety problems and risks within a process,develops corrective actions to respond to safety issues, and...