|FA228084||What is the coil wire insulation class of LC1F contactor. |
The coil insulation class for LC1F range contactor is class F.
|FA228083||Is there any workaround to use the powersuite configuration file into new firmware version 2.6 Tesys T relay which are compatible with SoMove software.|
Yes, it is possible.
If there is powersuite configuration file (*.impr) is stored on your PC, then open that powersuite file by click on Open with...
|FA228076||What is the a llowable temperature for GV2ME range of MPCB used in GV2MC01 enclosure. |
When GV2ME range of MPCB used with GV2MC01 enclosure, the allowable temperature limit for this combination is : +5*C to 40*C.
|FA228004||Is it possible to do fine tunning on Compact NSX MCCB with Micrologic trip unit 5/6 for long time protection setting by keypads.|
Yes, it possible to do fine tunning using keypads to set the long time protection Ir pick-up on a Compact NSX Micrologic trip unit 5/6.
User can set...
|FA227971||What is the Tightening Torque of power connections of Compact NSX 100...630A AC circuit breakers.|
The Tightening Torque of power connections of Compact NSX 100...630A AC circuit breakers is given in below attachment.
|FA228007||Is there any mounting plate available for replacement of TeSys LC1F115 or LC1F150 with LC1D115 or LC1D150 range of contactors.|
Yes, there is a mounting plate available for replacement of TeSys LC1F115 or LC1F150 with LC1D115 or LC1D150 range of contactors.
The ordering reference...
|FA228005||What are the consituents of TeSys LE1M35*** non-reversing D.O.L starters.|
The standard version of TeSys LE1M35*** non-reversing D.O.L comprises:
> 1 TeSys contactor LC1 K**,
> 1 TeSys thermal overload relay LR2 K,
> 1 green...
|FA228002||How to Troubleshoot a nuisance tripping on TeSys GV*** and LRD*** range of products.|
Please refer the below attached guide for troubleshooting a nuisance tripping on TeSys GV*** and LRD*** range of products.
|FA221915||What is the Tripping resistance of TeSys Thermistor protection relay LT2-SA***.|
The Tripping resistance of TeSys Thermistor protection relay LT2-SA*** is 1650 ... 4000 ohm.
|FA227970||What is the class and accuracy of current transformer (CT) to be used with EOCR3MZ**** relay.|
The CT class is 10P5 and accuracy for EOCR3MZ**** relay is shown below