|FA170509||Where is the Test Button resistor connected between the poles of Vigi iC60 devices (3P and 4P).|
The Test Button resistor is connected between the poles 2 and 3 of Vigi iC60 devices (3P and 4P).
Please refer the below diagram
|FA170508||What is the earth fault loop impedance values (Zs) for the Acti9 iC60 MCB’s.|
The earth fault loop impedance values for Acti9 iC60 are given in below table.
|FA170507||How many stop bits does the EGX support.|
All EGX devices use an 11-bit frame serial frame. 1 start-bit, 8 data-bits, and 1 or 2 stop bits
depending on the parity selection.
|FA170506||Is it possible to enable "Auto Scrolling" for the EM6400 series meter display.|
Auto Scroll allows the user to monitor a group of Display Pages sequentially, every 5 seconds, without constant key pressing.
There are three different...
|FA170505||Is there any difference in CT wiring of PM800 and PM200/PM700 for Three-Phase 3-wire Power Systems when using 2 CTs.|
For 3-wire, three-phase systems with 2 CTs, its required to connect terminal S2 = X2 of CT1 to the I2+ terminal of
the PM200/PM700 instead of the...
|FA22590||What is the selection criterion of Circuit Breakers for the Capacitor bank application.|
The selection should be done after derating the Circuit Breaker taking into consideration voltage variation and capacitors tolerances that could increase...
|FA170013||After running for a few seconds, Data Service will automatically stop without any prompts.|
Backfill can cause the symptom. If "ToTime" attribute is earlier than "FromTime" attribute in a backfill record. Data service will consider it as...
|FA170012||What is difference between floating point and static point licensing in Vijeo Citect.|
A client license can be static or floating depending on requirements
Static client license: For operators needing access to the system at all times,...
|FA170011||How to exit the vijeo citect from demo mode.|
When you start Vijeo Citect runtime it will check for the license key and if did not found any valid license then
automatically starts in demo mode....
|FA170008||How do I use Microsoft Windows Media Player ActiveX in Citect.|
You will need to set the Media Player ActiveX object property to specify the filename that needs be opened and also call the Play Method via Cicode: