|FA240937||Is it possible supply the fan with an external supply on ATV71HC31N4 drive.|
Yes, it is possible supply the fan with an external supply, for this you need to change the terminal and supplied the R, S, T, terminal.
|FA240936||Is it possible to run the Altistrt 22 Soft starter on 55°C ambient temperature.|
Yes, it is possible to run the Altistrt 22 on 55°C ambient temperatures.
For ambient temperatures between +40°C and +60°C, derate the nominal current...
|FA240935||Is it possible to do scaling on AI1, AI2 & AI3 Analog Inputs on Altivar 312 drives.|
Only, scaling of Analog Input AI3 is possible. Refer to attached file.
|FA240905||How can I communicate Vijeo Citect with PLC using OPC communication|
|FA240572||What will be the MTTF value of Compact NSX VIGI module.|
The MTTF value of Compact NSX VIGI module is 546 years.
|FA240575||What products will come with VIGILOHM Mobile fault locating kit.|
The VIGILOHM Mobile fault locating kit which comprises of below products:
1)a locating signal generator, XGR, supplied with 220 - 240 V AC
|FA240574||What will be the power loss of Acti 9 Vigi module.|
The power loss of Acti 9 vigi is shown below:
|FA240576||Is it possible to defeat the Door Interlock in Compact NS630b-1600 MCCB.|
It is possible to defeat the Door Interlock in Compact NS630b-1600 MCCB. The steps are shown in the attachments.
|FA238388||What is the staus indication of Network Status LED of IFE Ethernet interface for LV circuit breaker.|
The network status dual color LED, indicates the Ethernet network status as given below
|FA240661||Which pressure sensor we can select for use in Nitrogen gas environment.|
You can use our XMLA series to detect the nitrogen gas . The nitrogen is a neutral gaz,and you can control it without problem with the pressure switch...