|FA242185||How to establish the communication between TSXETY110 over Ethway and Vijeo Citect through OPC.|
Refer the attached Technote which guide how to configure the TSXETY110 over Ethway and also to fetch data upto Vijeo Citect over OPC.
|FA242182||what is the Attenuation limit of Coaxial cable RG6 and RG11.|
Below is the Attenuation limit of RG6 and RG11 at 1.544MHZ:
97-5750-000 RG6 cable has 1.18dB/100m (0.36dB/100ft) attenuation at 1.544MHz.
|FA242174||What will be the minumum frquency on which EOCR-3DM can work.|
The minimum frequency on which EOCR 3DMW work is 20Hz.
|FA242173||How to read 2 phases or 3 phase BCPM systems in ION Enterprise?|
The 2- and 3-phase measurements of BPCM are actually in the translator but which are "disable/hidden" by default.
To "enable/un-hide" it, you are...
|FA242171||What will be maximum current that can be directly connected to the iEM3110.|
The maximum current that can be directly connected to the iEM3110 is 63A.
|FA242172||What's the burden of BCPM power consumption|
The BCPM is fused at 500mA so that will be the absolute maximum it could draw, however we expect normal draw to be less than 100mA.
So if the voltage...
|FA242165||How to reset kWh on BCPM|
Write "10203" (Clear all KWH values to zero) to register "295"
|FA242164||Explanation for d.Prd in PM1000 series|
D.Prd stands for Demand Period, which is selectable by the user. In Pm1000/EM 6400 demand period is selectable ranging from 5 to 30 minutes, in steps...
|FA242140||What is the material for LA1DX and LA1DY auxillary contacts used in harsh industrial environments for Tesys D range contactors.|
The material for LA1DX and LA1DY is Gold - Single break with crossed bars.
|FA242139||Which combination block will be used between the GV2ME and the LP4K series contactors.|
The GV2AF01 is a combination block between the GV2ME and all K series contactors.