|FA273717||What is the sub assembly of XCKS149H29 limit switch.|
Sub assembly of XCKS149H29:
=>ZCKS1H29 + ZCKD49
|FA273689||What is the difference between ZB5AS56 and ZB5AS54 Emergency switching off pushbutton.|
ZB5AS56 is the same as a ZB5AS54. But the head of ZB5AS56 is blue colour.
Refer to ZB5AS54 data sheet in attachment.
|FA273659||What is the Mechanical durability of ZBE101.|
ZBE101 Mechanical durability is 5000000 cycles.
|FA273657||What is the life of incandescent bulb DL1CE012.|
Life of incandescent bulb DL1CE012 is 10000 hours.
|FA273775||What is the default IP address, username, and password for PowerLogic PM8000 series meter.|
The default IP address is 169.254.0.10.
The username and password are defined by your meter’s security configuration; if standard security is enabled,...
|FA273772||What are the measurement voltage inputs rated at for PowerLogic PM8000 series meter.|
Measured voltage: 57 to 400 V L-N / 100 to 690 V L-L (Wye) or 100 to 600 V L-L (Delta or Wye with unearthed neutral)
Frequency: 50/60 Hz ± 15%,
|FA273771||What is the rating of the current inputs for PowerLogic PM8000 series meter.|
Nominal 5 A (Class 0.2S) or 1 A (Class 0.5S)
Measured current: 50 mA to 10 A
Starting current: 5 mA
Withstand: 20 A continuous, 50 A @10 sec/hr, 500...
|FA273769||What are the control power input requirements in PowerLogic PM8000 series meter.|
120 to 300 V DC ± 10%
50/60 Hz ± 10% : 90 to 415 V ± 10%400 Hz: 90 to 120 V ± 10%
|FA273569||How is SF6 medium-voltage electrical equipment recycled.|
The equipment is first collected from the customer's site and delivered to a Schneider Electric Centre where it is dismantled. The various ferrous...
|FA273567||What is the service life of medium-voltage equipment|
The service life of medium-voltage equipment greatly depends on its conditions of use and on the environment in which it was used.