|FA169761||What does ‘Integr Inst’ means when looking at the trip history on a micrologic P.|
The message ‘ Integr Inst' means a tripping by the instantaneous self-protection built into the device that is called as DIN/DINF.
When such message...
|FA169760||Is there any temperature derating table available for Compact NSX DC PV circuit breaker.|
The temperature derating table for Compact NSX DC PV circuit breaker is attached below.
|FA169759||What is the maximum rated operational voltage (Ue) of Compact NSX DC PV MCCB.|
The maximum rated operational voltage of Compact NSX DC PV MCCB is 1000 VDC.
|FA169758||Is it required to remove the rating plug in Micrologic E of Masterpact NW/NT & Compact NS 630b … 1600 A circuit breakers while performing megger test.|
The Micrologic E has a different technology than that of Micrologic A, P and H.
The Micrologic E measures the voltage through a high impedance...
|FA169757||Is there any tripping curves available for Compact NSX DC PV circuit breaker.|
The tripping curves for Compact NSX DC PV MCCB are available and are attached below.
|FA169756||Does the Modbus Chassis Communication Module (CCM) support 2 wire RS485 communications.|
The Modbus Chassis Communications Module does support 2 wire RS485 communications.
The module can be configured by jumpering the IN+ and the OUT+...
|FA169755||What is the default baud rate , address and parity of Breaker Communications Module (BCM) and Chassis Communications Module (CCM).|
For the CCM the Default values are: Baud rate = 19.2 K , Address = 97, Parity = even
For the BCM the default values are: Baud rate = 19.2 K, Address...
|FA169754||What is the limit on Modbus multi drop connection for both the HMI port and also on the Modbus port in TeSys T.|
The limit on the left or the right port for TeSys T Modbus product is the same.
These features are defined by Modbus standard: maximum 1000 meters...
|FA169752||Is there any dual redundancy available with TeSys T’s offer.|
Yes, it is available with Ethernet Product only. This is the dual port technology which allows that.
The redundancy is for Ethernet Communication...
|FA169751||Is it possible to feed the supply from top (upstream) and bottom (downstream) in compact NSX range MCCB.|
Compact NSX circuit breakers can be supplied from either the top or the bottom, even when equipped with a Vigi
earth-leakage protection module, without...