|FA242119||M580 CPU cannot establish communication using either USB or Ethernet with BMXXBE1000 extender module installed.|
It is a normal behavior of the M580 architecture that if user install the BMXXBE1000 extender module in the rack then they has to take care of below...
|FA242117||In which condition 232 LED is blinking on Quantum CPU 140CPU67160 and what will be the modbus ID in Hot standby CPUs.|
If "232" is blinking on CPU LCD then it means there is a Serial port activity is there for RS-232 and data is polling from or to devices/application.
|FA242188||How to Disable the FTP and HTTP security in 140NOE77101 and 14077111 module.|
These services can be disabled in Security Option available in Unity pro Ethernet communication configuration setting.
Take a note these services...
|FA242185||How to establish the communication between TSXETY110 over Ethway and Vijeo Citect through OPC.|
Refer the attached Technote which guide how to configure the TSXETY110 over Ethway and also to fetch data upto Vijeo Citect over OPC.
|FA242182||what is the Attenuation limit of Coaxial cable RG6 and RG11.|
Below is the Attenuation limit of RG6 and RG11 at 1.544MHZ:
97-5750-000 RG6 cable has 1.18dB/100m (0.36dB/100ft) attenuation at 1.544MHz.
|FA242174||What will be the minumum frquency on which EOCR-3DM can work.|
The minimum frequency on which EOCR 3DMW work is 20Hz.
|FA242173||How to read 2 phases or 3 phase BCPM systems in ION Enterprise?|
The 2- and 3-phase measurements of BPCM are actually in the translator but which are "disable/hidden" by default.
To "enable/un-hide" it, you are...
|FA242171||What will be maximum current that can be directly connected to the iEM3110.|
The maximum current that can be directly connected to the iEM3110 is 63A.
|FA242172||What's the burden of BCPM power consumption|
The BCPM is fused at 500mA so that will be the absolute maximum it could draw, however we expect normal draw to be less than 100mA.
So if the voltage...
|FA242165||How to reset kWh on BCPM|
Write "10203" (Clear all KWH values to zero) to register "295"