|FA238759||What are the recommendation to use Altistart 48 Soft starter for Submersible motor application.|
ATS48 is suitable for Submersible motor application.
However you need to consider the following general recommendation for this application.
|FA238758||Why the input current of the ATV61HC50N4 drive is lower than the output current.|
ATV61HC50N4 drive comes as standard with DC Choke.
The DC Choke decreases the amplitude of harmonics.
Then, the RMS current decrease.
That is why;...
|FA238757||What are the check points of SLF1 fault for Altivar 32 drive.|
SLF1 is the modbus communication fault.means communication interruption on the Modbus bus.
Points to check in case of (SLF1):----
|FA238756||What is the maximum cable distance from Altistart 48 Soft Starter to motor.|
There is no distance limit clearly fixed for the Maximum Cable length,
The official limit guaranteed is about 100m.
However, we know applications...
|FA238754||Altivar 61 under monitoring, there is a motor power but the data is in terms of percentage. What does this percentage means.|
[Motor power] (OPr) displays as a % of the rated motor power in the Monitoring Menu.
Example: 10 KW motor is connected to 10KW ATV61 drive.
|FA238751|| Is it suitable to select Altivar 61 drive for Submersible motor application.|
ATV61 is suitable for Submersible motor application.
However, following are the general recommendation for this application.
1. Insulation level of...
|FA238749||Is it possible to order XCSZP7015.|
The XCSZP7015 and the XCSZP1 part number are the 2 parts of the XCSDMP7015 coded magnetic switch (complete sensor with XCSZP1 magnet)
|FA238748||How to simulate the thermal sensor on Altivar 71 drive.|
We propose a simulation of the thermal sensor with a potentiometer of 5Kohms. When you changed the value from potentiometer the value on the THD must...
|FA238747||waht are the number and size of each conductors in the wire of XCSDMP7002 coded magnetic switch.|
Cables used in the XCSDMP7002 switches => PVC cable, black jacket, 6 wires of 0.25mm2 each.
|FA238737||ZBZVM and ZBZVG LED suppressor for light block have two cables,How long are the cables.|
The length of the cables is 60mm.