|FA234107||How we can power up the HMI XBTN200 when we do not have port power supply available in the connected PLC or device such as M218 PLC as this HMI requires power supply to its RJ45 communication port only.|
If you are using device such as PLC TM218 to communicate with XBTN200 which do not have power supply on its Communication port to power up the HMI....
|FA232984||APC Switched Rack PDUs - any pending outlet commands are lost when PDU Network Management Interface is rebooted |
If an APC Switched Rack PDU's Network Management Interface is rebooted (manually by the user, or automatically due to network watchdog timer...
|FA231199||Are there Windows or Linux drivers for the NBAC0226 USB to serial cable. |
There are no drivers available for the NBAC0226 serial to USB cable.
NetBotz Serial devices...
|FA226483||KVM1116P, KVM2116P, and KVM2132P KVM Switches using standalone WinClient and Java Client - Compatibility/Video Issue|
When using the WinClient or Java Client with my KVM1116P, KVM2116P or KVM2132P IP KVM Switch, why is my video distorted (as seen below)?
|FA22997||What are the recommended characteristics for a Modbus Jbus RS485 / Com / ABT network cable?|
The recommended characteristics of the RS485/Modbus cable are: twisted pair with tinned copper braid shielding. Minimum overlap: 65%. Gauge: AWG 24....
|FA23749||What is the tightening torque for the terminal extensions and spreaders for Compact NS100 to 630 circuit-breakers.|
The tightening torque for the terminal extensions and spreaders for Compact NS100 to 630 circuit breakers is:
10 Nm for Compact NS100.
15 Nm for...
|FA23629||What are the different types of electrical and hydraulic (fluid) connection for XMLA and XMLB pressure switches?|
For XMLA and XMLB pressure switches, the last 3 digits of the product code (S11, S12, S13 or S14) determine the thread of the electrical and hydraulic...
|FA23786||Can the SDE contact be fitted into a Masterpact NT or NW switch disconnector.|
The SDE contact does not perform any function on a Masterpact switch disconnector and therefore it's not fitted nor is it available as an option.
|FA23748||What is the part number of the fixed Front Connection snap-in nuts for the Compact NS100 to 630 circuit-breakers.|
The part number of a set of 12 fixed front connection snap-in nuts is:
29234 for Compact NS100.
30554 for Compact NS160... 250.
These parts are...
|FA27970||What is the meaning of the terms 2P2d, 3P3d, 4P3d, 4P4d, 4P3d+N/2 and 4P3d+OSN on the Compact NSX circuit-breaker trip units.|
The first number corresponds to the number of poles.
The second number corresponds to the number of protected poles.
The first letter stands for Pole.