|FA21081||What is the reference number for the Modbus Plus Tap Spare plastic caps.?|
The little plastic caps come along with the Modbus Plus Tap and they cannot be ordered separately.
|FA27988||Can I replace a broken toggle on an NS / NSX circuit-breaker or switch.?|
No, the toggle on the breaker frame cannot be replaced as the toggle is integral to the breaker frame.
The breaker frame needs to be replaced.
|FA22583||What is the full name of the abbreviation 'STR' trip unit ? .|
The abbreviation 'STR' has a very old origin. The first generations of trip units were called Statimax and 'STR' refers to "Statimax Trip Release".
|FA27969||How can I obtain the manufacturing date of the Compact NS or NSX circuit-breakers ? |
To obtain the manufacturing date of Compact NS or NSX circuit-breakers, read the screen-printed marking at the top of the front panel.
The code P07351,...
|FA23075||Can I install a potentiometer, part number SZ1RV1202, in an XACA enclosure?|
No. There are two reasons preventing a potentiometer, part number SZ1RV1202, from being installed in an XACA enclosure:
1. An SZ1RV1202 potentiometer...
|FA256219||What is EEF1 fault on Altivar 71 drive.|
EEF1 is a control EEprom Fault and at starting, the microprocessor on the application board tries to read and write to the EEPROM. If it is impossible,...
|FA256218||Is push button & receiver of wireless and batteryless package XB5RMA04 comes as factory-paired.|
If you order XB5RMA04 pack, then following item comes on this pack and it is already factory-paired: -----
(1) => 1 number wireless and battery less...
|FA255317||For the setting of the PTC probe in the fault management, if we set it to Motor On, will the sensing of the LI6 happen when the Altivar 71 drive sends run command to motor. |
If you set PtCL to [Motor ON], then it will monitor the resistance Value when the VSD sends a run command to motor.
Input for a...
|FA255313||What is the wiring resistance of Preventa safety module XPSAXE feedback loop.|
Maximum wiring resistance of the XPSAXE feedback loop between Y1-Y2 & Y1-Y3 = 70 ohm
|FA255311||What are the probable causes of E-19 fault on Altivar 212 drive.|
E19 is a CPU communications error (Communication error between control CPUs).
- Verify the internal cable connection between the boards.
- Check the...