|FA172145||What is the part code for a Zelio Smart Relay with an Analogue Output?|
You will need to use SR3B101BD (or other 24vDC modular relay) + SR3XT43BD I/O extension module which has the analogue output.
|FA172159||What is the part code for a lead for XS618B1PAM12?|
The code is XZCPV1141L2 for a straight plug with 2m PVC lead
The XZCPV1241L2 is an angled plug with 2m PVC lead
Longer lengths may be available,...
|FA172188||What code is an enclosure suitable for an Emergency stop?|
XALK01 is a single 22mm hole enclosure with a light grey base and yellow lid.
XALK01H29 is the same but also has Emergency Stop engraved on the lid....
|FA172195||What is the part code if I need a ZB4BG2 key switch, but with a different key then the standard 455 key?|
One option is a ZB4BG212. This has a 421E key.
|FA172201||What code is a light block for the XALD or XALK enclosures?|
Depending on the voltage and colour required the codes are ZALVB* for 24vAC/DC, ZALVG* for 48-120vAC or ZALVM* for 230vAC
|FA237150||What is the difference between BMXRMS008MPF and BMXRMS008MP.|
There is a difference of memory size between the two.
BMXRMS008MP can store 8MB data.
BMXRMS008MPF card that you can use the data file storage...
|FA237084||Do we have any product in our Phaseo ABL range which shows display and relay output function.|
In our Phaseo ABL8 power supply range we have the input & output supply healthy indication LED`s available with auto & manual output selection switch.
|FA32985||What is the difference between a VPIS and a VDS (SM6, RM6 power ON pilot light)?|
VPIS (Voltage Presence Indicator System): According to standard IEC 61958 the purpose of a VPIS is to signal a voltage presence. If a lamp is unlit,...
|FA23919||What are the values of the 1P breaking capacities of GV2P circuit-breakers in IT earthing system?|
The values below are the breaking capacities of GV2P circuit-breakers operating on an IT earthing system at 400 V 50 Hz, as demonstrated by pole-by-pole...
|FA141655||Will Zelio Soft 2 V4.5 work on Windows 7 64 bit?|
Yes, the only current issue that arises is when it comes to communicate between the PC/Laptop and the Zelio Logic Relay, if you use the USB cable...