|FA221986|| Does Altivar 71/61 drive with Passive filter draw high input current during no load. |
Passive filters are adjusted for nominal load. In case of no load or low load, reactive power (from passive filter capacitors) increases. That is...
|FA225487||Can we use both 2NC and 1NO block together on the light block ZB6ZB**B .|
You can not mount both 2NC and 1NO block together on this ZB6ZB**B (fixing collar + contact block + LED) , as you can mount maximum 2 contact block...
|FA222287||What is meaning of "bridge mode" in 140NOM2xx00 module|
The 140 NOM 2xx 00 are modbus plus option modules which has modbus plus as well as a modbus connector on them. A bridge mode capability in the module...
|FA221988|| Ethernet communication card - VW3A3320 for Altivar 61 / Altivar 71 drives supports which protocols|
Ethernet communication card - VW3A3320 supports protocols (1) Ethernet I/P and (2) Modbus TCP/IP. When this card is inserted in ATV61/ ATV71 drives,...
|FA221987|| With which firmware versions of Altivar 61 / Altivar 71 drives, Ethernet communication card VW3A3320 is compatible|
Ethernent communication card - VW3A3320 is supported by Altivar 61 only with firmware versions V5.8 and above, Altivar 71 with firmware version...
|FA177671||What are the logic addresses for display parameters - O01 to O50 of controller inside that can be displayed on graphic display of altivar 61 / 71|
Logic addresses of display parameters O01 to O50 starts from 6401 and is up to 6450 respectively.
|FA31975||Can a third party photo cell be used with the light sensitive switches.|
No, the light sensitive switches are designed to be used with the photo cells supplied with them.
|FA177638||At what temperature value temperature controlled switch is operated in protected type braking resistors designed for Altivar 312 drives|
Protected braking resistors VW3A701 to VW3A705 integrated with temperature controlled switch that becomes operational at 120’C temperature
|FA176909||Is it required to provide an isolation in each side of Acti 9 C60NA-DC direct current switch-disconnector.|
Yes, It is recommended to provide a Spacer clips of 9 mm in each side to provide isolation for Acti 9 C60NA-DC direct current switch-disconnector.
|FA176908|| Is it possible to use TeSys electric trips (GVAU*, GVAS*, GVAX* with old GV2M* motor protection circuit breaker. |
Yes, it is possible to use TeSys electric trips (GVAU*, GVAS*, GVAX* with old GV2M* motor protection circuit breaker.