|FA176393||What is the fault aux contact for a GV2 which has a normally open contact|
The part code GVAD1010
|FA178907||Is the Aux Contact 29450 compatible with NS and NSX MCCB's?|
Yes, fully compatible with either NS or NSX MCCB's, as is the 29452 Aux Contact.
|FA178908||Are the NS shunt or undervoltage trips compatible with NSX bodies?|
Yes, the shunt or undervoltage trips used in NS MCCB's will also fit NSX MCCB's.
|FA225851||What code is a mechanical interlock for the 4pole LC1D1150046 contactor?|
LA9D11502 will fit the 4p LC1D115 and LC1D150 contactors
|FA172875||Can I buy a replacement enclosures for the LE1M range|
Replacement enclosures are not available for the LE1M range
|FA22775||How many UA150 ATS controller can be used with one DC150 module.|
Only one UA150 controller can be used per DC150 and its Digipact address must be set at 14-14.
|FA22592||Will there be any problem if the MX coil (shunt trip) of NS100 to NS630 is continuously kept powered up.|
With the newer design technology there will be absolutely no problems if the MX coil (shunt trip coil) of NS100 to NS630 is continuously kept powered...
|FA12121||Which are the Drives in Altivar 31 Standard Range that has in-built Fan Units.|
All the Drives in the Altivar 31 Standard Range has in-built Fan Units, except ATV31H018M2, ATV31H037M2, ATV31H055M2 and ATV31H075M2 Drives do not...
|FA22774||What are the characteristics of STR13MAE (MAE500) trip unit used in Compact NS630 circuit breaker.|
The Compact NS630 fitted with the STR13MAE trip unit is named: NS630MAE500.
The old MA500 trip unit was designed with mechanical feature. The new...
|FA22583||What is the full name of the abbreviation 'STR' trip unit.|
The abbreviation 'STR' has a very old origin. The first generations of trip units were called Statimax and 'STR' refers to "Statimax Trip Release".