|FA172875||Can I buy a replacement enclosures for the LE1M range|
Replacement enclosures are not available for the LE1M range
|FA22775||How many UA150 ATS controller can be used with one DC150 module.|
Only one UA150 controller can be used per DC150 and its Digipact address must be set at 14-14.
|FA22592||Will there be any problem if the MX coil (shunt trip) of NS100 to NS630 is continuously kept powered up.|
With the newer design technology there will be absolutely no problems if the MX coil (shunt trip coil) of NS100 to NS630 is continuously kept powered...
|FA12121||Which are the Drives in Altivar 31 Standard Range that has in-built Fan Units.|
All the Drives in the Altivar 31 Standard Range has in-built Fan Units, except ATV31H018M2, ATV31H037M2, ATV31H055M2 and ATV31H075M2 Drives do not...
|FA22774||What are the characteristics of STR13MAE (MAE500) trip unit used in Compact NS630 circuit breaker.|
The Compact NS630 fitted with the STR13MAE trip unit is named: NS630MAE500.
The old MA500 trip unit was designed with mechanical feature. The new...
|FA22583||What is the full name of the abbreviation 'STR' trip unit.|
The abbreviation 'STR' has a very old origin. The first generations of trip units were called Statimax and 'STR' refers to "Statimax Trip Release".
|FA22613||What is the maximum rated DC current at DC voltage for the auxiliary contacts of C60.|
The maximum rated DC Voltage and DC Current for the Category DC12 (IEC 60947-5) auxiliary contacts OF, SD, OF+SD/OF, OF.S (Reference - 26924,26927,26929,26923)...
|FA22617||What is the maximum rated AC current at AC voltage for the auxiliary contacts of C60.|
The maximum rated AC Voltage and AC Current for the Category AC12 (IEC 60947-5) auxiliary contacts OF, SD, OF+SD/OF, OF.S (Reference - 26924, 26927,...
|FA22619||What is the maximum Insulation Voltage of Miniature Circuit Breaker (MCB) C60. |
The maximum Insulation Voltage of Miniature Circuit Breaker (MCB) C60 is 500V.
|FA156051||What are the Share-UPS and Interface Expander modes of operation?|
What are the Share-UPS and Interface Expander modes of operation?
UPS Device Management