|FA176898||Is there any Comb busbar available in Acti 9 range for circuit breakers that can accomodate auxiliaries iOF/iSD also.|
Yes, In Acti 9 range there is a special comb busbar for circuit breakers with 9 mm auxiliaries and they have a 9 mm gap for inserting iOF and iSD.
|FA176893||Is the Acti 9 Reflex iC60 available in a direct-current version.|
The Reflex iC60 is available only in an alternating-current version.
|FA176897||Is it possible to use TeSys auxiliary contact block LA1KN** (screw clamp terminal) with LC1K*5** and LP1K*5** (solder pin version) contactors. |
Yes, it possible to use TeSys auxiliary contact block LA1KN** (screw clamp terminal) with LC1K*5** and LP1K*5** (solder pin version) contactors.
|FA176750||What is the difference between 46996 and 33195 toggle extension. |
46996 is the toggle extension as the picture & reference is mentioned in the attached catalog page and 33195 is the reference of additional toggle...
|FA176594||What is the part number of Programmable contacts M6C for Compact NS>630 range of circuit breaker|
The same M6C reference 47404 like for Masterpact NW range air circuit breaker can be used with Compact NS>630 range of MCCB.
|FA176553||Can the old timer block LA*D* of TeSys D2 range be used for TeSys D range of contactors. |
The old design timer block LA2D**or LA3D** of TeSys D2 range are not compatible with TeSys D range of contactors.
|FA176554||Is it possible to use MN undervoltage release in combination with C60 MCB and C60 Vigi module.|
The interpretation is like that the MCB will be fitted over Vigi module and the electrical auxiliaries like MN undervoltage release are left hand...
|FA173231|| Kindly confirm if clear incandescent bulb DL1CE130 can be used on 120VDC. The product catalog did not mention the type of voltage, but in the datasheet it was only for AC.|
Yes, you can use this clear incandescent bulb DL1CE130 with 120-130 VDC 2.4W also, actually an incandescent bulb has not polarity, that means you...
|FA22590||What is the selection criterion of Circuit Breakers for the Capacitor bank application.|
The selection should be done after derating the Circuit Breaker taking into consideration voltage variation and capacitors tolerances that could increase...
|FA166495||Is it possible to use the auxiliary switch ref. 29450 (OF/SD/SDE) with Compact NSX DC-PV range MCCB.|
All accessories and auxiliaries of the Compact NSX DC PV breaker are identical to the Compact NSX DC range
and it is also mentioned in the catalog.