|FA171254||What kind of Technology is used in Type 1 and Type 2 class of surge arresters.|
The Type 1 (PRF1 surge arresters) use “encapsulated air-filled spark gap “ type technology without arc device while as the
Type 2 (PRD surge arresters)...
|FA171253||Are Multi 9 and Acti 9 contactors CT/iCT in compliance with the EN 61095 standard.|
Our Acti9 and Multi9 range iCT/CT are fully compliant with EN61095.
The EN61095 is the dedicated standard for contactors for household and similar...
|FA171252||What is the classification of Acti 9 range of products for Corrosive atmospheres.|
For Corrosive atmospheres the classification is 3C2 (urban regions with industrial activities, heavy traffic) as per IEC 60721-3-3 for
Acti 9 range...
|FA171250||What is the Dielectric resistance of Acti 9 smartlink prefabricated cables.|
The Dielectric resistance of Acti 9 smartlink prefabricated cables is1kV/5min.
|FA171076||Would digital inputs of LXM32 servo range drives take effect when SoMoveLite control panel access is enabled.|
When SoMoveLite control panel access is enabled, it is exclusive control and will be given top priority. So, effect
of activating digital inputs physically...
|FA171072||What is the difference between pre-cabled connectors (1) XZ CP1141L2 and (2) XZ CP1169L2 when both are 4 pins, female, straight and M12 connectors.|
Difference between (1) XZ CP1141L2 and (2) XZ CP1169L2 is as below.
==> XZCP1141L2 is a straight, 4 pins M12 Female connector with PUR cable of...
|FA170718||In a linear load application, is IT earthing acceptable to use AC type C60 Vigi module.|
For IT earthing system must use ASi or ASiE devices to avoid nuisance tripping of C60 Vigi modules.
The main reason is due to Neutral line is not...
|FA170716||Is it necessary to connect the Acti9 range of contactor (iACT24) to the 230VAC power supply.|
The 24VDC is just used to send the command, from Acti 9 Smartlink or a PLC. To be able to energize the coil of the
associated contactor, the iACT24...
|FA170714||What is maximum length of the cable between MCB and Acti9 Smartlink.|
The cable length between an input of the Acti9 Smartlink and any device connected is limited to 20 meters.
|FA170712||What's the burden of BCPM power consumption.|
The BCPM is fused at 500mA so, that will be the absolute maximum it could draw, however we expect normal draw to be less than 100mA.
So if the...