|FA169755||What is the default baud rate , address and parity of Breaker Communications Module (BCM) and Chassis Communications Module (CCM).|
For the CCM the Default values are: Baud rate = 19.2 K , Address = 97, Parity = even
For the BCM the default values are: Baud rate = 19.2 K, Address...
|FA169752||Is there any dual redundancy available with TeSys T’s offer.|
Yes, it is available with Ethernet Product only. This is the dual port technology which allows that.
The redundancy is for Ethernet Communication...
|FA169751||Is it possible to feed the supply from top (upstream) and bottom (downstream) in compact NSX range MCCB.|
Compact NSX circuit breakers can be supplied from either the top or the bottom, even when equipped with a Vigi
earth-leakage protection module, without...
|FA169750||What is the memory capacity of the processor used on the Micrologic 5 or 6 E trip units.|
The microcontroller has 512 Kbytes in Flash memory and 32 kBytes in RAM on the Micrologic 5 or 6 trip units.
|FA169749||Is it possible to use the 3 poles NSX circuit breakers with 3 pole Vigi module on a single phase application.|
The Vigi module can be used in a single-phase configuration for a 3P type. The Vigi works in single-phase between two phases,
The test push button...
|FA169748||What is the definition of the term OSN on micrologic electronic trip units.|
OSN (Over Size Neutral) means that the neutral protection is 1.6 times greater than the phase protection.
This type of trip unit is used if there...
|FA169747||How to obtain the manufacturing date code of the Compact NS or NSX circuit-breakers from the MCCB.|
To obtain the manufacturing date of Compact NS or NSX circuit-breakers, read the screen-printed marking at the top of the front panel.
|FA168471||How can I look at the compilation errors in Vijeo Citect.|
When you compile your Vijeo Citect project then a message appears and shows warnings & error messages, if you again want to re-check
|FA168470||Where did I find the Citect.ini file in my Windows 7 system.|
The citect.ini files in a Windows 7 System will be found in the given below location.
C:\ProgramData\Schneider Electric\Vijeo Citect 7.20\Config
|FA168464||Does Altivar 212 has options of Ethernet card for communication.|
Altivar 212 doesnot have Ethernet card as an option. However you can use ethernet gateways for communication devices on Ethernet protocol.