|FA166609||When using ATS22, what is difference between motor overload alarm and motor overload trip (OLF).|
When motor thermal state as calculated by starter is reached to 110%, motor overload alarm is triggered but when motor
thermal state continues to...
|FA166608||When over sized selection of ATS22 is mandatory. How to do oversize selection.|
The Altistart 22 rating is limited to 3.5 IcL. IcL is the nominal current of the Altistart 22. If the application requires a
higher rated starting...
|FA166607||What does “tBS” mean in case of ATS22 or ATS48 soft-starter. Does it indicate fault state of soft-starter.|
“tBS” does not indicate any fault state of soft-starter but as it name suggests it is “Time before re-starting”.
It can be set in unit of seconds....
|FA166606||What minimum power of motor could be operated with ATS22 soft starter.|
ATS22 is having inbuilt bypass contactor and its switching takes place only when Imotor (Actual Motor current)
of In (Motor rated current set with...
|FA166604||Are Zx-function keys multifunctional.|
Normally, Zx function Keys work as navigation keys. They can also be used in a control diagram while developing logic with
zeliosoft2. In this configuration,...
|FA166565||What cables to be used to connect Local PC to SoMachine software.|
TCS XCNA MUM3P:This USB cable is suitable for short duration connection like quick updates or retrieving data values.
BMX XCA USBH045: Grounded...
|FA166521||Pinout details of Modbus junction box- VW3A8306TF**.|
Pinout details of Modbus junction box- VW3A8306TF** is as below,
|FA166508||Is it mandatory to use heatsink and thermal interface with SSR P range of SSR (Solid State Relays).|
SSR P (Panel mounting type SSR) are not with inbuilt heatsink compare to the integrated heat-sink
of SSR D (Din rail mounting type SSR) rerlays.
|FA166507||What is timeout error while communicating with PM1000 & DM6000 meter and what are the reasons for this error.|
When a master like EGX, ION Enterprise ,System (PC) sends a query & doesn't receive any response from the Meter
within the wait time then the error...
|FA166505||For PM1000 meters, when are external CTs and/or PTs required.|
External CT is required when the load current to be measured is greater than 6A.
An external PT is required when input voltage greater than 480V