|FA166499||What are the factory default settings in DM6000 series.|
The factory default settings in DM6000 series is as below,
|FA166497||Is it possible to use the reference LA9D901 with the reference LADR, LADS2 etc.|
The LADS2, LADR* and LADT* are time delay auxiliary contact blocks.
Each reference respond to distinct need, however theirs external design are identically.
|FA166496||What is the maximum and minimum height of the bracket LA7F901 and LA7F902 used with LC1F range Contactor.|
Refer below the heights of these brackets:--
> LA7F901: Hmin= 51 mm / Hmax=84 mm
> LA7F902: Hmin= 64 mm / Hmax=106 mm
|FA166495||Is it possible to use the auxiliary switch ref. 29450 (OF/SD/SDE) with Compact NSX DC-PV range MCCB.|
All accessories and auxiliaries of the Compact NSX DC PV breaker are identical to the Compact NSX DC range
and it is also mentioned in the catalog.
|FA166493||Is it possible to have an operation Counter in Easypact MVS range ACB.|
Yes, it is possible to use same Operation Counter of Masterpact NW in Easypact MVS range ACB.
|FA166492||What is the difference between MSU unit & MN undervoltage release of C60 range MCB.|
MSU is dedicated to monitor power supply voltage and trips RCB in case this voltage turns higher
than values safe for the appliances. MN will trip...
|FA166491||Is it possible to use the same auxiliary contact shunt trip of C60 range with C60H RCBO.|
Yes, it is possible to use the same auxiliary functions as the C60 circuit breaker, to install on the left of the C60H RCBO.
|FA166490||What is the tolerance on the nominal voltage for the C60 electrical auxiliaries.|
As per the IEC 60947-2 standard, the tolerance for the electrical auxiliaries for the LV breakers is 0.85 of minimum Un
and 1.1 of maximum Un.
|FA166489||Is it possible to use the under voltage release and the shunt trip for the C60H circuit breaker at 400 Hz.|
For MN under voltage release, there is a specific part number ref. 26959 for 400Hz, 115V application.
For MX shunt trip, it does not operate under...
|FA166488||Is it possible to use C60 comb-busbar on DC application.|
Yes, the comb-busbar for C60 range MCB can be used under DC network. And the rated insulation voltage = 500 V