|FA22617||What is the maximum rated AC current at AC voltage for the auxiliary contacts of C60.|
The maximum rated AC Voltage and AC Current for the Category AC12 (IEC 60947-5) auxiliary contacts OF, SD, OF+SD/OF, OF.S (Reference - 26924, 26927,...
|FA22614||What is the derating table for the Combo Busbar of C60 as per temperature.|
Find attached the derating table for the Combo Busbar for C60 as per temperature.
|FA21085||Is it possible to configure ring topology with Modbus and Modbus Plus communication networks.|
Modbus and Modbus Plus networks support line and star topology only. These networks cannot be configured in ring topology.
However, it is possible...
|FA22582||What is the KA rating of 29372 and 32623 Busbar Adapters for Compact NS/NSX<630 Circuit Breaker.|
The breaking capacity (KA rating) of the system with the Busbar Adapters 29372 and 32623 connected with Compact NS/NSX
|FA22584||Why does the display light of Micrologic 6.2 trip unit of Compact NSX not glow even when the load reading is displayed. |
Unlike other range of Micrologic the backlighting or display light of Micrologic 6.2 is not self powered by the primary current.
A separate external...
|FA22770||Is the installation of 31097 locking kit same as the 31088 in Interpact source changeover system.|
Yes, the installation of the 31097 & 31088 locking kits is the same, as all key locks have been designed to achieve locking in the OFF position.
|FA22635||What is the thickness of the Steel sheet metal of Blokset Panel.|
The Steel sheet metal thickness used in Blokset Panel is as per the below table:
Blokset Steel sheet metal thickness
|FA22583||What is the full name of the abbreviation 'STR' trip unit.|
The abbreviation 'STR' has a very old origin. The first generations of trip units were called Statimax and 'STR' refers to "Statimax Trip Release".
|FA22599||What is meant by Thermal image in Compact NSX.|
The model representing the conductor heat rise is constructed according to the calculation of a thermal image. It allows the thermal state of the...
|FA22655||What is the difference between mechanical Interlock EZ2LB0601 & EZ2LB0602 of LC1B Contactor.|
EZ2LB0601 comes without bearing & EZ2LB0602 comes with bearing, this is the main difference between these interlocks.
EZ2LB0602 interlock usually...