|FA170616||Is it possible to operate or configure ATV303 drive with remote HMI |
Yes, it is possible to operate and / or to configure ATV303 drive by means of remote HMI Part reference VW3A1006.
|FA170611||Does “dIS” on display of lexium servo drive indicates fault. How to overcome it.|
“dIS” on display does not indicate fault state of lexium servo drive but it is one of the states of servo drive.
dIS stands for Switch ON Disabled....
|FA170610||When Lexium 32 range of servo drive goes into the “QUICK STOP”.|
Lexium 32 range of servo drive goes into the QUICK STOP under two conditions
If servo drive meet with an error of class 1 or class 2.
|FA170609||In Lexium range drive the permissible range of motor shaft movement if absolute position is to be retained while servo drive is powered off.|
Permissible range of motor shaft movement is +/ - 0.25 revolution from the position at which motor shaft position was
at the moment servo drive was...
|FA170608||In Altivar range of drives ,display of current (A) is blinking on 7 –segment LED display. What does this mean.|
Blinking of Current (A) displayed on 7-segment LED display indicates that drive has reached to the current limitation.
This occurs when current drawn...
|FA170509||Where is the Test Button resistor connected between the poles of Vigi iC60 devices (3P and 4P).|
The Test Button resistor is connected between the poles 2 and 3 of Vigi iC60 devices (3P and 4P).
Please refer the below diagram
|FA170508||What is the earth fault loop impedance values (Zs) for the Acti9 iC60 MCB’s.|
The earth fault loop impedance values for Acti9 iC60 are given in below table.
|FA170507||How many stop bits does the EGX support.|
All EGX devices use an 11-bit frame serial frame. 1 start-bit, 8 data-bits, and 1 or 2 stop bits
depending on the parity selection.
|FA170506||Is it possible to enable "Auto Scrolling" for the EM6400 series meter display.|
Auto Scroll allows the user to monitor a group of Display Pages sequentially, every 5 seconds, without constant key pressing.
There are three different...
|FA170505||Is there any difference in CT wiring of PM800 and PM200/PM700 for Three-Phase 3-wire Power Systems when using 2 CTs.|
For 3-wire, three-phase systems with 2 CTs, its required to connect terminal S2 = X2 of CT1 to the I2+ terminal of
the PM200/PM700 instead of the...