|FA28095||What are the part numbers of the BA9S type bulbs for XB4/XB5 pushbutton controls?|
For Harmony XB4/XB5 22 diameter control and signalling units, whether: LED lamps, incandescent lamps, neon lamps, there are part numbers with BA9s...
|FA24940||Do the GS1 or GS2 disconnect switches come with fuses?|
No, because the fuse is linked to the application, eg:
fast-acting semi-conductor fuses for electronic loads
aM fuses for motor loads
|FA23920||What is the operation of the GV2AD fault signalling contacts of the GV2 circuit-breakers?|
GV2ME, GV2P, GV2L, GV2LE, GV3P and GV3L circuit-breakers can be fitted with the following optional fault indicating contact blocks:
|FA23663||What are the part numbers of the replacement contact sets for LC1F power contactors?|
Spare parts required for each pole of LC1Fxx contactors are as follows:
2 fixed contacts
1 moving contact
|FA23278||In what type of control station can I install control and signaling units from the Harmony style 5 range?|
Harmony style 5 range (XB5) buttons can be used on the front panel of the following control stations:
XALK, XALD: plastic control stations,
|FA23212||Is "remote reset" function available for GV2 / GV3 / GV7 circuit breakers?|
No remote reset is available for GV2/GV3/GV7 circuit breakers. Remote tripping, using shunt trips, is available but no reset.
Remote resets are...
|FA22942||Where can I find the characteristics of the LC1D contactors?|
You will find all the characteristics of LC1Dxx contactors on the Tesys web page:
The section Downloads has documents ( Catalogues, Brochures, Catalogue...
|FA23032||What is an EVERLINK connection and what are its advantages?|
TESYS Everlink contactor
TeSys Everlink is an enhancement to Schneider Electric's motor starter solutions, offering combinations of 2 or 3 products...
|FA22954||What power supplies should I use to supply light curtains?|
Schneider Electric guarantees the correct operation of its light curtains if they are powered with the following modules:
|FA22755||How can I perform the "start test" function on an XUSLA light curtain monitored by an XPSMP configurable module?|
Test mode function: This function is neither mandatory nor critical since the XUSLx light curtain has a continuous self-test function (type 4 safety).