|FA248969||What is the maximum numbers of drives allowed on RSTP loop for Altivar 61 / Altivar 71 drives |
Maximum number of drives allowed on a RSTP loop is 32 with ATV61 / ATV71.
With 32 drives it is ensured that standard IEEE802.1 is respected and a...
|FA248968||Which drives from altivar range supports RSTP protocol management|
Altivar 61 and Altivar 71 range of drives with Ethernet network communication card - VW3A3320 when inserted supports RSTP management.
|FA248734||What temperature value does the thermal protection of detuned reactor is set.|
The thermal protection of our detuned reactor is set up at 155°C, with a tolerence of +/- 5°C.
|FA248735||What will be the tolerance limits for inductance for detuned reactor.|
The tolerance limits for inductance for detuned reactor should be +/-5%. The measured value should be within this limit.
|FA248736||What is the voltage tolerance level for NSX ME VIGI.|
In NSX ME VIGI the tolerances applicable to the voltage are +10% and -15%. That means the vigi works perfectly between 170V and 484V but be careful...
|FA248770||Do we have load and line reversibility with Acti9 RCBO (Integrated or with Vigi type ).|
Acti9 RCBO or Integrated VIGI can be can be connected upstream or downstream without deterioration in the performance.
|FA248737||What reference comes with 29350.|
The 29350 consists of two references i.e. 29349 and 29352.
|FA248769||In SoMachine, while trying to add function "schedGetProcessorLoad" to check processor load, build error message appears - Unknown type: 'RTS_IEC_RESULT' occurs|
To check processor load in SoMachine, function "schedGetProcessorLoad" is used.
Before adding this function, user have to add library "cmpSchedule"...
|FA248768||Is it possible to get processor load for SoMachine range controller |
Yes, it is possible to get current running processor load for SoMachine range controllers.
Follow below steps with SoMachine project.
|FA248766||SoHVAC can not be connected to M168 controller. When trying to connect, message appears " Connected hardware is unknown" Do you want to proceed with download? Finished: can not open COM port|
Such type of behavior is possible when using SoHVAC software version V3 and the usage of COM port for M168 controller
particularly with windows 7...