|FA176587||Can our TeSys contactors be used for utilisation category AC-5.|
Yes. Our TeSys contactors can be used for utilisation category AC-5.
The Utilisation Catgory AC-5 has following sub-categories:
AC 5a - Switching...
|FA176583||What are the characteristics of the Mitop coil used in SF6 circuit breaker.|
The Mitop coil actuates the opening mechanism of the poles to trip the circuit breaker.
It comprises a low energy consumption electromagnet.
|FA176728|| How much memory does EGX300 support|
The EGX300 modbus to Ethernet gateway which has the Log equipment maintenance activities via. the EGX web interface having 256Mb Memory for logging,...
|FA176727||What is the purpose of CET850 software and where can i download the same.|
Purpose: CET850 is used for the advanced configuration of the IEC61850 communication. Some basic configuration can be done using SFT2841, but CET850...
|FA176726||How to resolve an error message "SFTCommon Library is not installed in this system" while running CET850 software.|
Unfortunately, the CET850 software does not come with those SFTCommon-... files. You should be able to correct this by downloading another piece of...
|FA176724||What are the current input characteristics of PM5350 power meter.|
Current Input characteristics of PM5350 are Continuous 20 A,10 sec/hr for 50 A,1 sec/hr for 500 A.
|FA176723||What is the difference between UL and IEC standard |
The IEC (International Electrotechnical Commission) and UL (Underwriters Laboratories Inc.) standards differ significantly.
IEC standards specify...
|FA176594||What is the part number of Programmable contacts M6C for Compact NS>630 range of circuit breaker|
The same M6C reference 47404 like for Masterpact NW range air circuit breaker can be used with Compact NS>630 range of MCCB.
|FA176555||Can TeSys D timer block LADT* and LADR* be used for old TeSys D2 range of contactors.|
The TeSys D timer block LADT* and LADR* are compatible for old TeSys D2 range of contactors.
|FA176553||Can the old timer block LA*D* of TeSys D2 range be used for TeSys D range of contactors. |
The old design timer block LA2D**or LA3D** of TeSys D2 range are not compatible with TeSys D range of contactors.