|FA275536||Which minimum version of Vijeo Citect SCADA I have to upgrade so that I can use it on Windows 7 Operating System.|
You needs to upgrade Vijeo Citect SCADA software version to minimum Vijeo Citect SCADA V7.1 SP4 or above to use on Windows 7 .
|FA275535||With VJC 7.40 , i am using language change configuration in my project and for some texts like (@Stop) automatically showing STOP during SCADA runtime. How to resolve this problem.|
This problem of texts showing Uppercase letters can be resolve by adding the below INI parameter :
[Language]CaseSensitive = 1
|FA275534||Using HMISCU8B5 can I communicate TM3XTYS4 module to HMISCU8B5|
You can not be able to communicate TM3XTYS4 module with HMI SCU as this TM3XTYS4 is a TM3 expansion module which can be connected to TM3 expansion...
|FA275532||In historian configuration manager server it is showing Login failed error. What could be the reson for this error.|
This error mostly occurred due to system name changed and that creates the login problem of the SQL database.
Kindly change the SA login details...
|FA275531||While exporting huge data from Clear Scada using the ODBC query on Excel or MS Access, we encountered "Query time out" error, how can we change this query timeout in Clear SCADA.|
To remove this timeout error, you need to chnage the SQL Query parameters in Clear SCADA as shown below :
Query Row limit
Query Size Limit
|FA274823||In Modicon M221, does it come with the necessary accessories (connector, cable etc) for connecting Built-In Analog Input, or customer requires additional accessories to connect to these two AI channels.|
Connector for Built-In Analog Input along with equipped cable is supplied with Modicon M221 controller. It is a dedicated connector and cannot be...
|FA272879||Can i use Vijeo designer v6.2 outside SoMachine v4.1 without a valid Vijeo designer license|
When you launch Vijeo designer v6.2 from SoMachine v4.1, then VJD takes the license from SoMac. However, If you intend to use VJD v6.2 seperately,...
|FA273880||What is the maximum numbers of instances for %SEND_RECV_MSG function block|
Maximum numbers of 16 instances can be included in project for %SEND_RECV_MSG function block.
|FA273879||Does M200 controller support ASCII communication for RS-232 physical interface|
M200 controller as standard include 1 serial port - SL1 that supports only RS-485 physical interface. So, RS-232 physical interface is not possible...
|FA273792||TM238 PLC with ATV61 via CANOpen. From the hardware configuration in SoMachine software, there is no ATV61 in remote device list. Onlt ATV31, ATV312, ATV71 can be found. What is reason & how to solve this|
This is known behavior that SoMachine v3.1 and / or SoMachine v4.1 can not manage Device DTM for Altivar 61 due to some issue which will be corrected...