|FA240940||What is the programming parameter of Motor pole on Altivar 212 drive.|
The programming parameter of Motor Pole on ATV212 is F856.
Program F856 => 2 [4 poles]
So, 2 means, motor have 4 poles. It means Motor...
|FA240947||How to take backup in concept as ".asc" extension.|
".asc" file can be extract through conept convertor execution program named "Dbconv.exe" available in Concept directory. Refer the attached video...
|FA240939||Is Altivar 312 drives confirms the IEC 60721-3-3 standard.|
On ATV312 drives, a coated card comes as standard (IEC 60721-3-3 Classes 3C2).
|FA240938||Soft starter ATS22 is tripped on bPF fault after giving stop command. Output contactor is connected with ATS22 output. What will be the reason of tripping.|
bPF means Bypass contactor detected fault.
There is an output contactor connected with ATS22 output. So, this fault is appearing because the output...
|FA240937||Is it possible supply the fan with an external supply on ATV71HC31N4 drive.|
Yes, it is possible supply the fan with an external supply, for this you need to change the terminal and supplied the R, S, T, terminal.
|FA240936||Is it possible to run the Altistrt 22 Soft starter on 55°C ambient temperature.|
Yes, it is possible to run the Altistrt 22 on 55°C ambient temperatures.
For ambient temperatures between +40°C and +60°C, derate the nominal current...
|FA240935||Is it possible to do scaling on AI1, AI2 & AI3 Analog Inputs on Altivar 312 drives.|
Only, scaling of Analog Input AI3 is possible. Refer to attached file.
|FA240905||How can I communicate Vijeo Citect with PLC using OPC communication|
|FA240572||What will be the MTTF value of Compact NSX VIGI module.|
The MTTF value of Compact NSX VIGI module is 546 years.
|FA240575||What products will come with VIGILOHM Mobile fault locating kit.|
The VIGILOHM Mobile fault locating kit which comprises of below products:
1)a locating signal generator, XGR, supplied with 220 - 240 V AC