|FA170509||Where is the Test Button resistor connected between the poles of Vigi iC60 devices (3P and 4P).|
The Test Button resistor is connected between the poles 2 and 3 of Vigi iC60 devices (3P and 4P).
Please refer the below diagram
|FA170508||What is the earth fault loop impedance values (Zs) for the Acti9 iC60 MCB’s.|
The earth fault loop impedance values for Acti9 iC60 are given in below table.
|FA170507||How many stop bits does the EGX support.|
All EGX devices use an 11-bit frame serial frame. 1 start-bit, 8 data-bits, and 1 or 2 stop bits
depending on the parity selection.
|FA22590||What is the selection criterion of Circuit Breakers for the Capacitor bank application.|
The selection should be done after derating the Circuit Breaker taking into consideration voltage variation and capacitors tolerances that could increase...
|FA170012||What is difference between floating point and static point licensing in Vijeo Citect.|
A client license can be static or floating depending on requirements
Static client license: For operators needing access to the system at all times,...
|FA170011||How to exit the vijeo citect from demo mode.|
When you start Vijeo Citect runtime it will check for the license key and if did not found any valid license then
automatically starts in demo mode....
|FA170003||What are the changes in client licenses for Vijeo Citect V7.30.|
With the release of new Vijeo Citect V7.30 the distinction between Web and non-Web client versions has been removed.
The difference between the Control...
|FA169761||What does ‘Integr Inst’ means when looking at the trip history on a micrologic P.|
The message ‘ Integr Inst' means a tripping by the instantaneous self-protection built into the device that is called as DIN/DINF.
When such message...
|FA169760||Is there any temperature derating table available for Compact NSX DC PV circuit breaker.|
The temperature derating table for Compact NSX DC PV circuit breaker is attached below.
|FA169759||What is the maximum rated operational voltage (Ue) of Compact NSX DC PV MCCB.|
The maximum rated operational voltage of Compact NSX DC PV MCCB is 1000 VDC.