|FA168470||Where did I find the Citect.ini file in my Windows 7 system.|
The citect.ini files in a Windows 7 System will be found in the given below location.
C:\ProgramData\Schneider Electric\Vijeo Citect 7.20\Config
|FA168464||Does Altivar 212 has options of Ethernet card for communication.|
Altivar 212 doesnot have Ethernet card as an option. However you can use ethernet gateways for communication devices on Ethernet protocol.
|FA168243||What is the meaning of 1:100 speed range in Altivar 71 drive.|
Speed range is the ratio of the output maximum frequency/minimum frequency where the nominal torque is available.
Example: For a 50Hz motor
|FA168242||What is the options of braking resistor for Altivar 71 range.|
Refer to attached file forthe part number of braking resistor for Altivar 71 range.
|FA168009||Can the GV3 range MPCB be operated by a door interlockable external handle.|
Yes, it is possible by using of the GV3AP01 & GV3AP02.
|FA168008||Is the terminal shield used in Compact NS range MCCb compatible with NSX range of MCCB. |
Terminal shields are fully compatible between the Compact NS and Compact NSX ranges.
|FA168007||Is it possible to connect a 3 Pole Compact NSX breaker to use for single phase application.|
If you need to protect a single phase with a NSX in 3P you can connect the load (phase 1) to the pole 1 and
the load (neutral) to the pole 3. Pole...
|FA168006||Is it possible to use the Compact NS plug-in base with Compact NSX plug breaker.|
Compact NS base can be used for Compact NSX circuit breaker, but reverse is not possible.
The plug-in base:
> Of a Compact NS may be used for Compact...
|FA168005||What is the power consumption for Micrologic 5 or Micrologic 6 used with Compact NSX range MCCB. |
For micrologic 5/6, the power consumption typical value is 30 mA for 24Vdc.
|FA167818||What are the part numbers of line choke for Altivar 312 range.|
Refer to attached file for the part numbers of line choke for Altivar 312 range.