|FA166504||Can the firmware in a Energy Meter (ELF3200/EM6400/PM1200/DM6200) be upgraded.|
The firmware in any Conzerv Meter (ELF3200/EM6400) or Schneider-branded Conzerv Meter (DM6200/PM1200) cannot be upgraded.
|FA166503||Do I need DISABLE the File and Printer sharing option of my PC to get ION Enterprise Web Reporter to work.|
The File and Printer Sharing option must be disabled in ION Enterprise systems installed on OS .
This must be done during the install of ION Enterprise V...
|FA166502||What is the maximum number of registers the Modbus Device Importer (MDI) can configure and support.|
Maximum is 255 registers per module.
4095 modules per manager.
|FA166501||Can the VLT Ref 16060 (analogue voltmeter) be used on DC voltages.|
VLT ref 16060 is usable for AC voltages only within the range of 50-60 Hz. You cannot use it on DC voltages.
|FA166499||What are the factory default settings in DM6000 series.|
The factory default settings in DM6000 series is as below,
|FA166497||Is it possible to use the reference LA9D901 with the reference LADR, LADS2 etc.|
The LADS2, LADR* and LADT* are time delay auxiliary contact blocks.
Each reference respond to distinct need, however theirs external design are identically.
|FA166496||What is the maximum and minimum height of the bracket LA7F901 and LA7F902 used with LC1F range Contactor.|
Refer below the heights of these brackets:--
> LA7F901: Hmin= 51 mm / Hmax=84 mm
> LA7F902: Hmin= 64 mm / Hmax=106 mm
|FA166495||Is it possible to use the auxiliary switch ref. 29450 (OF/SD/SDE) with Compact NSX DC-PV range MCCB.|
All accessories and auxiliaries of the Compact NSX DC PV breaker are identical to the Compact NSX DC range
and it is also mentioned in the catalog.
|FA166493||Is it possible to have an operation Counter in Easypact MVS range ACB.|
Yes, it is possible to use same Operation Counter of Masterpact NW in Easypact MVS range ACB.
|FA166492||What is the difference between MSU unit & MN undervoltage release of C60 range MCB.|
MSU is dedicated to monitor power supply voltage and trips RCB in case this voltage turns higher
than values safe for the appliances. MN will trip...