Main rangeKaedra product or component typeWeatherproof enclosure enclosure typeEnclosure for modular device with interface accessories included with enclosure1 plate for 65 x 85 power outlets1 terminal block 32 holes1 terminal block 4 holes1 terminal block support3 marking kits3 wiring straps4 plates for push-button controls Complementary enclosure mountingSurface number of 18 mm modules per row12 total number of 18 mm modules36 number of horizontal rows3 electrical insulation classClass IIDouble insulation number of openings of interface4 number of plates4 for push-button controls1 for 65 x 85 power outlets provided equipment3 marking kit3 wiring strap1 plate for 65 x 85 power outlet4 plate for push-button control1 terminal block 4 holes1 terminal block support1 terminal block 32 holes type of front coverReversibleTransparent [In] rated current125 A type of railDIN number of pre-cutouts PG ISO17 number of terminal blocks1 with 32 outgoers1 with 4 outgoers distribution block outgoers18 x 10 mm²18 x 16 mm² locking options descriptionOptional keylock enclosure materialHousing : self-extinguishing polymer base dimension90 x 100 mm width448 mm height610 mm depth160 mm colourDoor : transparent greenEnclosure : light grey ( RAL 7035 ) Environment standardsEN 50102EN 50262IEC 60439-3IEC 60529IEC 60695-2-1IEC 670 fire resistance650 °C conforming to IEC 60695-2-1 IP degree of protectionIP65 conforming to IEC 60529 IK degree of protectionIK09 conforming to EN 50102 Environmental characteristics (UV)UV resistant class 3 conforming to ISO 4582 2010Ultraviolet degradation test conforming to ISO 4892-2 2013 overvoltage categoryII ambient air temperature for operation-25...60 °C Contractual warranty Warranty period18 months
Documents & DownloadsLanguage
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsEnclosure for modular switchgear with interface 3 rows + 4 openings 36 modulesEnclosure for modular switchgear with interface 3 rows + 4 openings 36 modules
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.