Main range of productActi 9 product or component typeShunt trip release device short nameMXV [Uc] control circuit voltage110...240 V AC 50/60 Hz110 V DC 9 mm pitches3 Complementary range compatibilityVigi NG125Acti 9 NG125LMAActi 9 NG125NAActi 9 NG125 [Ui] rated insulation voltage690 V AC 50/60 Hz conforming to EN/IEC 60947-5-1 [Uimp] rated impulse withstand voltage8 kV conforming to EN/IEC 60947-5-1 local signallingAction indicator mounting modeFixed mounting support35 mm symmetrical DIN rail height106 mm width25 mm depth80 mm net weight0.038 kg electrical durability10000 cycles conforming to EN/IEC 60947-5-1 connections - terminalsPlate terminal - 1 cable(s) 0.5…2.5 mm² - rigidPlate terminal - 1 cable(s) 0.5…1.5 mm² - flexiblePlate terminal - 1 cable(s) 0.5…1.5 mm² - flexible with ferrulePlate terminal - 2 cable(s) 2.5 mm² - flexiblePlate terminal - 2 cable(s) 2.5 mm² - rigidPlate terminal - 2 cable(s) 1.5 mm² - flexible with ferrule wire stripping length10 mm tightening torque1 N.m compatibility codeMXV Environment standardsEN/IEC 60947-5-1 product certificationsLCIEASEFAKEMAASTA IP degree of protectionIP20 B conforming to EN/IEC 60947-5-1IP4 conforming to EN/IEC 60947-5-1 pollution degree3 conforming to EN/IEC 60947-5-1 overvoltage categoryII tropicalisation2 conforming to EN/IEC 60947-5-1 relative humidity95 % at 55 °C ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…85 °C Offer Sustainability Sustainable offer statusGreen Premium product REACh Regulation EU RoHS DirectiveCompliant
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS RegulationChina RoHS declaration
Product out of China RoHS scope. Substance declaration for your information
Circularity Profile WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
Documents & DownloadsLanguage
User guideSizeAdd to My DocumentsCADSizeAdd to My DocumentsEnd of Life InformationSizeAdd to My Documents
Technical FAQsNo results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.