Main range of productActi 9 product nameActi 9 iPRC device short nameIPRC product or component typeSurge arrester number of protected lines2 surge arrester typeTelecom protection Complementary remote signallingWithout surge arrester technologyGDT + diode [In] rated current0.45 A at 45 °C [Ue] rated operational voltage130 V AC nominal discharge currentCommon mode: 10 kA (L/PE)Differential mode: 10 kA (L/N) [Uc] maximum continuous operating voltageCommon mode: 130 V AC L/PECommon mode: 185 V DC L/PEDifferential mode: 130 V AC L/NDifferential mode: 185 V DC L/N maximum [Up] voltage protection levelDifferential mode <160 V type 2 L/NCommon mode <200 V type 2 L/PE output voltage limitsCommon mode: < 300 V at 1 kV/µsDifferential mode: < 300 V at 1 kV/µs [I total] discharge current10 kA mounting modeFixed mounting support35 mm symmetrical DIN rail 9 mm pitches2 height90 mm width18 mm depth66 mm product weight25 g colourWhite materialPA6 response time< 500 ns connections - terminalsScrew clamp terminal0.2…4 mm² rigidScrew clamp terminal0.2…2.5 mm² flexibleScrew clamp terminal0.2…2.5 mm² flexible with ferrule wire stripping length8 mm tightening torque0.8 N.m Environment standardsEN 61643-21IEC 61643-21 product certificationsXDSL compliance IP degree of protectionIP40 (modular enclosure) conforming to IEC 60529IP20 conforming to IEC 60529 IK degree of protectionIK05 conforming to IEC 62262 relative humidity5…90 % operating altitude2000 m ambient air temperature for operation-25…60 °C ambient air temperature for storage-40…85 °C Offer Sustainability REACh Regulation EU RoHS DirectivePro-active compliance (Product out of EU RoHS legal scope)
EU RoHS Declaration
Mercury freeYes RoHS exemption information China RoHS Regulation WEEEThe product must be disposed on European Union markets following specific waste collection and never end up in rubbish bins Contractual warranty Warranty18 months
Documents & DownloadsLanguage
CADSizeAdd to My DocumentsiPRC for Telecom network surge Arrester (Version 1.0)iPRC for Telecom network surge Arrester (Version 1.0)
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.