Main rangeTeSys product nameTeSys LC1D.K product or component typeCapacitor duty contactor device short nameLC1DFK device applicationControl contactor applicationPower factor correction poles description3P power pole contact composition3 NO [Ue] rated operational voltage<= 690 V AC 50/60 Hz for power circuit reactive power rating7 kvar at 220...240 V AC 50/60 Hz <= 55 °C13 kvar at 400...440 V AC 50/60 Hz <= 55 °C21 kvar at 660...690 V AC 50/60 Hz <= 55 °C control circuit typeAC 50/60 Hz [Uc] control circuit voltage220 V AC 50/60 Hz auxiliary contact composition1 NO + 2 NC instantaneous for control circuit electrical durability300000 cycles at Ue 400 V200000 cycles at Ue 690 V mounting supportDIN railPlate standardsIEC 60947-4-1 product certificationsCCCCSAUL connections - terminalsPower circuit : connector 1 cable(s) 2.5 mm² - cable stiffness: flexible - with cable endPower circuit : connector 2 cable(s) 1.5 mm² - cable stiffness: flexible - with cable endPower circuit : connector 1 cable(s) 4 mm² - cable stiffness: solid - without cable endPower circuit : connector 2 cable(s) 4 mm² - cable stiffness: solid - without cable end tightening torquePower circuit : 1.7 N.m - on connector operating rate240 cyc/h Complementary auxiliary contacts typeType mechanically linked (1 NO + 2 NC) conforming to IEC 60947-5-1 Environment IP degree of protectionIP20 conforming to IEC 60529 protective treatmentTH conforming to IEC 60068-2-30 ambient air temperature for operation-5...60 °C ambient air temperature for storage-60...80 °C operating altitude3000 m without derating in temperature height130 mm width45 mm depth117 mm product weight0.53 kg Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profileAvailable Product end of life instructionsNeed no specific recycling operations
Documents & DownloadsLanguage
CADSizeAdd to My DocumentsContactor 12,5/16,7 kVAR; TeSys D
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.