Main rangeTeSys product nameTeSys F product or component typeReversing contactor device short nameLC2F contactor applicationMotor controlResistive load utilisation categoryAC-1AC-3 device presentationPreassembled with reversing power busbar poles description3P power pole contact composition3 NO [Ue] rated operational voltage<= 1000 V AC 50/60 Hz<= 460 V DC [Ie] rated operational current200 A (<= 40 °C) at <= 440 V AC AC-1115 A (<= 40 °C) at <= 440 V AC AC-3 motor power kW30 kW at 220...240 V AC 50/60 Hz80 kW at 660…690 V AC 50/60 Hz55 kW at 380...400 V AC 50/60 Hz59 kW at 415 V AC 50/60 Hz59 kW at 440 V AC 50/60 Hz65 kW at 1000 V AC 50/60 Hz75 kW at 500 V AC 50/60 Hz control circuit typeAC 40...400 Hz [Uc] control circuit voltage220 V AC 40...400 Hz [Uimp] rated impulse withstand voltage8 kV overvoltage categoryIII [Ith] conventional free air thermal current200 A at <= 40 °C Irms rated making capacity1150 A AC conforming to IEC 60947-4-1 rated breaking capacity920 A conforming to IEC 60947-4-1 [Icw] rated short-time withstand current1100 A <= 40 °C 10 s640 A <= 40 °C 30 s520 A <= 40 °C 1 min400 A <= 40 °C 3 min320 A <= 40 °C 10 min associated fuse rating125 A aM at <= 440 V200 A gG at <= 440 V average impedance0.37 mOhm at 50 Hz - Ith 200 A [Ui] rated insulation voltage1000 V conforming to IEC 60947-4-11500 V conforming to VDE 0110 group C power dissipation per pole5 W : AC-3 interlocking typeMechanical mounting supportPlate standardsEN 60947-1EN 60947-4-1IEC 60947-1IEC 60947-4-1JIS C8201-4-1 product certificationsABSCCCCSADNVLROS (Lloyds register of shipping)RINARMRoSULCB connections - terminalsControl circuit : screw clamp terminals 2 cable(s) 1...2.5 mm² - cable stiffness: flexible - with cable endPower circuit : connector 1 cable(s) 95 mm²Control circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: flexible - without cable endControl circuit : screw clamp terminals 2 cable(s) 1...4 mm² - cable stiffness: flexible - without cable endControl circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: flexible - with cable endControl circuit : screw clamp terminals 1 cable(s) 1...4 mm² - cable stiffness: solid - without cable endControl circuit : screw clamp terminals 2 cable(s) 1...4 mm² - cable stiffness: solid - without cable endPower circuit : lugs-ring terminals 1 cable(s) 95 mm²Power circuit : bar 2 x ( 20 x 3 mm) tightening torqueControl circuit : 1.2 N.mPower circuit : 10 N.m operating time23...35 ms closing5...15 ms opening mechanical durability10 Mcycles operating rate2400 cyc/h at <= 55 °C Complementary control circuit voltage limits0.35...0.55 Uc at 55 °C drop-out 50/60 Hz0.85...1.1 Uc at 55 °C operational 50/60 Hz inrush power in VA550 VA at 20 °C (cos ϕ 0.3) 50 Hz660 VA at 20 °C (cos ϕ 0.3) 60 Hz hold-in power consumption in VA45 VA at 20 °C (cos ϕ 0.3) 50 Hz55 VA at 20 °C (cos ϕ 0.3) 60 Hz heat dissipation12...16 W Environment IP degree of protectionIP20 front face with shrouds (ordered separately) conforming to IEC 60529IP20 front face with shrouds (ordered separately) conforming to VDE 0106 protective treatmentTH ambient air temperature for operation-5...55 °C ambient air temperature for storage-60...80 °C permissible ambient air temperature around the device-40...70 °C operating altitude3000 m without derating in temperature mechanical robustnessVibrations contactor closed 6 Gn, 5...300 HzShocks contactor open 9 Gn for 11 msVibrations contactor open 2 Gn, 5...300 HzShocks contactor closed 15 Gn for 11 ms height162 mm width345 mm depth171 mm product weight6.86 kg Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructions Contractual warranty Warranty period18 months
Documents & DownloadsLanguage
BrochureSizeAdd to My DocumentsCertificateSizeAdd to My DocumentsDeclaration of conformitySizeAdd to My DocumentsEnd of Life InformationSizeAdd to My DocumentsMarine certificateSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.